No. The primary function of a circuit breaker is to protect the wire. A 15 amp breaker has a 14 gauge wire and a 20 amp breaker uses 12 gauge wire. If you replace a 15 amp with 20 amps, the breaker is sized larger than the wire, and the wire can over- heat to a potentially dangerous point before the breaker would trip. In order to upgrade the breaker AND the wire would have to be replaced.
About This Community
|Asked: 9/27/19, 10:05 PM|
|Seen: 8 times|
|Last updated: 9/27/19, 10:06 PM|